CONTENTS CONCRETE REPAIR CORROSION CONTROL GROUTS & ANCHORS PROTECTIVE COATINGS INDUSTRIAL FLOORING SURFACE TREATMENTS JOINT SEALANTS CONCRETE JOINTING JOINT FILLERS WATERPROOFING WATERSTOPS ROOFING TIMBER FLOORING ALPHABETICAL INDEX 357 Summary of tests to AS1530.4 Expansion Joints on concrete (120mm thick) Report Number Test Type Joint Width Joint Depth 1 or 2 sided Resistance to passage of Insulation limit of 181C flame temperature rises Rating Exova: 2259500.3 Expansion Joint 10mm 10mm 1: fire side only No failure at 241 mins 146 mins 240/120 (Concrete) Expansion Joint 40mm 20mm 1: fire side only No failure at 241 mins 68 mins 240/60 Penetration and perimeter seals on fire rated gypsum board Report Number Test Type Joint Width Joint Depth 1 or 2 sided Resistance to passage of flame Insulation limit of 181C temperature rises Rating Exova: 2254400 A--vertical control joint 20mm 16mm 2: fire and non fire side No failure at 155 mins 155 mins 120/120 (plasterboard) B--deflection head joint 20mm 16mm 2: fire and non fire side No failure at 155 mins 130 mins 120/120 (115mm thick C--40mm brass pipe 10mm 16mm 2: fire and non fire side No failure at 155 mins 35 mins 120/30 steel stud plaster D--D2 GpB cable install 20mm 16mm 2: fire and non fire side failed at 104 minsϷ 37 mins 90/30 board wall) E--D1 GpA cable install 40mm 16mm 2: fire and non fire side failed at 142 mins 38 mins 120/30 F--150mm copper pipe 10mm 16mm 2: fire and non fire side No failure at 155 mins 8 mins 120/0 G--100mm brass pipe 10mm 16mm 2: fire and non fire side failed at 68 minsϸ 7 minutes 60/0 Notes: 1 Ignition of the cable sheathing 2 Failure of cap on pipe at 68 minutes venting furnace gases Low insulation figures are indicative of heat transfer via the pipe and/or cable not the sealant. Penetrations in masonry, concrete and Autoclaved Aerated Concrete Report Number Opinion Covers various pipes up to 150mm diameter and includes ferrous metals as well as brass and copper with opinion that same results would occur with same configurations in jointsCovers various cable configurations BUT for Covers header and vertical joints for different substrates such as Masonry, Hebel and Concrete as well a gypsum as tested Masonry walls/Concrete walls and Hebel ACC walls for same fire ratings Exova: 25050-03 (opinion) 1 hour Penetration in single layer 16mm fire rated gypsum board Report Number Test Type Joint Width Joint Depth 1 or 2 Sided Integrity Insulation Rating Metal Pipes 10mm 16mm* 2: Fire and non fireside 60 mins 0 60/- Cables 10mm 16mm* 2: Fire and non fireside 60 mins 30 mins 60/30 Exova 27179-00 Notes: 1 layer of 16mm fire rated plasterboard either side of a stud wall. Total wall thickness of 83mm. To achieve the 1 hour rating the sealant must have a minimum depth of 16mm achieved by chamfering the joint in a triangular configuration from the pipe or cable to the face of the board. Refer specific penetration systems in Report 2254400. 2 hour Penetrations in fire rated gypsum board where cables and pipes are sheathed in Rockwool Report Number Test Type Joint Width Joint Depth 1 or 2 Sided Integrity Insulation Rating 27279-01 1 layer fireboard 20mm 16mm 2 sided 60 mins 60 mins 60/60 2 layers fireboard 20mm 16mm 2 sided 120mins 120 mins 120/120 1 layer fireboard 20mm 16mm 2 sided 60 mins 60 mins 60/60 2 layers fireboard 20mm 16mm 2 sided 120 mins 120 mins 120/120 Metal Pipes PVC Cables Airbourne Sound Transmission ATF Report # Wall description Joint' Details Sound Rating Rw Filler Wall No sealant in Slots Slots filled with Fireblock 67 2061 67(-1,-3) 35 Filling Slots (Joints) in Multilayered plasterboard Filler (internal) wall 9.95m2 in area 12mm x 12mm x 12 metres total length (Max expected sealant usage for wall of this area) Storage Store unopened sausages below 300C in a cool dry place away from direct sunlight. Unopened sausages can be stored for 24 months from the date of manufacture. Opened sausages may skin and form a lump near the opening. Discard any lumps or skin and remaining product can be used.
32857 Parchem Technical Data Compendium 2015_Crop4emag.pdf
To see the actual publication please follow the link above